About Induction Heating
What electrical service is required?
Electrical service for your Ambrell system
Your EKOHEAT system accepts 3 phase line-voltages from 360 to 520 Vrms. The
internal fuse selections anticipate the corresponding current levels for your equipment.
See your operator's manual for more information.
- Plan a 4-wire routing scheme for three phases and one protective earth ground.
- We recommend that you install a fused disconnect switch (not supplied by Ambrell) in the branch circuit supplying the equipment. Base your selection of fuses on the equipment nameplate data.
- Determine correct disconnect fusing and wire gauge.
- Place the disconnect near the RF generator, and in sight of the operator